DL100 | Emergency eye wash
Emergency eye wash
EYE WASH AND EMERGENCY SHOWERS
Conform to norms: UNI 9608 - UNI 10271 - DIN 12899 - ANSI - European Directive 93/42/CEE - PR EN 15154 Installation: Installation of shower head: between 2100/2300 mm. in height from the floor (see Norm UNI 9608). Installation of eye-wash nozzles: between 800/1150 mm. in height from the floor (see Norm UNI 9608). For installation use only trained and authorised staff. It is recommended to periodically and regularly check the efficiency of the emergency devices. For the assembly: Follow the instructions carefully! It is recommended to periodically and regularly check the efficiency of the water discharge. Keep the floor dry to avoid accidents caused by stagnant water. Choose the location: It is necessary to install emergency showers and eye-wash in the vicinity of the work area. It is also important that they are accessible and easily usable (within 7 / 8 meters). It is recommended to keep the emergency showers and eye-wash far from electrical plants and / or electricity sources. To allow easy access to emergency showers and / or eye-wash avoid accumulating material in the vicinity. Any barrier to access must be immediately removed. It is recommended to install a number of emergency units appropriate to the amount of people who will be using them.
Wall mounted eye-wash with aerated flow. Showers and bowl in ABS. Operated by a lateral push lever.